Take a closer look at the physical colocation options presented by our Vapor Edge Modules. We deploy these modular data centers in edge locations, with different sizes and capacities optimized for specific site and market conditions. These detailed specifications provide the information you need to plan your Kinetic Edge deployments in any market.
NEMA 3R+ Construction One-Piece Roof/Rain Canopy
Double Gasketed Exterior Access Doors
Full LED internal lighting
Forklift and Crane compatible base structure
Rack 1 – 47RU 600mm Width x 1200mm Depth
Rack 2 – 47RU 600mm Width x 1200mm Depth Zones
Rack 1 – 4 x L6-30 1ph 208V
Rack 2 – 4 x L6-30 1ph 208V
20kW DX Cooling System @ N, 12kW at 2N
Separate Cooling System access
Hot-Swappable N+1 Supply Fan System
Fully independent 12kW DX Systems for concurrent maintainability below 12kW.
Ships Complete and Tested
8ft x 12ft
Minimum 4ft in front of Doors and Electrical Enclosures
Minimum 2ft in front of Condenser
200A Single Phase 240V Service
2 x 4in Conduits
480V 3Ph 60Hz (315A MCA/350A Input Breaker)
165 kW critical IT load @ 110°F Ambient; 1 full Vapor Chamber, 6 Wedge Racks at 36 RU each, supporting up to 24 separate tenants.
19,500 CFM @ 72°F (25°F ?T Target)
Eaton 93PM 150 kVA, 480V 3ph Input – 120/208V 3ph Output.
24,000 CFM @ 72°F (25°F ?T Target).
Schneider Electric Galaxy VM 225kVA, 480V 3ph input – 208V 3ph output.
We will reach you with your email address soon.
Thank you for the time!